Use instructions Room thermostat
Bimetallic room thermostat for heating and air-conditioning instalations
Thermal, electrical and mechanical features Breaking capacity on opening contact, 10A-250V A.C.(ohmic load)Differential:0.5K
Temperature's scale adjustment
After almost two days from the installation, to obtain a precise scale adjustment, measure the room temperature with a reference thermometer, placed aside to reach the same value of the thermometer, We suggest to install the equipment at at about1.5mt from the floor and far from any heat source.
● Accelerating resistance with voitage to 220V-250V a.c.
● This thermostat is provided with an accelerating resistance which mustbe absolutely connected in order to obtain the regulation's performances.
● The terminal 4has thus to be connected to the neutral according to the diagram shown on the cover.
● This connection allows also the working of the pilot lamp which indicates the operation of the heating.